This article will focus on how pvDesign's power factor tool works and on the general understanding of the concept behind it.
Grid connection requirements are becoming stricter each day. This can be embodied by the application of a power factor to your energy plant resulting in less useful (active) power output. As a consequence, reactive power compensation has become crucial and should be studied adequately for each solar PV project.
In pvDesign, we are always working on implementing new features that reflect the industry trend. With such a goal in mind, we provide a feature that allows you to define a power factor for your PV plant.
Before we delve deeper into this topic, just bear in mind that there are three main terms to understand before working with the power factor. These are the apparent power, active power, and reactive power. The apparent power is the total power which is divided into both active and reactive power. When talking about a PV plant’s output, the term that we tend to refer to is the active power. The active power is the actual useful power that your PV plant will produce, whereas the reactive power will be the portion that will always be there but won’t be used for electricity generation. The power factor, to a certain extent, defines the active power portion from the total amount of apparent power.
Now, with this part cleared, we can hop onto the software pvDesign and see what it has to offer.
First thing’s first, as you can see below in Figure 1, you can opt to define the power factor at the substation’s input or output.
Figure 1 - Power factor in pvDesign.
Once you define your required power factor value at the selected point, pvDesign will give you the resulting power factor at the inverter output. It will also calculate the reactive power portion which is provided in the Energy Report. With the reactive power calculated, pvDesign will automatically start compensating for it by installing additional inverters to cover the entire DC field. But this is not where it all ends!
In order to understand this part better, we should first cover all the different parameters that pvDesign offers and which in turn affect the inverter’s resulting power factor. In pvDesign, you can enable the transformer losses for both the substation and the power stations. And since the software allows you to simulate the basic design of a substation, you can opt between a switching and breaking station or a substation (as shown below in Figure 2).
Figure 2 - Interconnection facilities in pvDesign.
Does changing the Transformer Losses affect my Power Factor?
We will now explain how varying these aforementioned parameters affects the resulting power factor inside pvDesign while scratching the surface on why such changes occur.
pvDesign allows you to modify the transformer’s iron and copper losses. Modifying these losses (either in the substation or in the power stations) will affect both the active and reactive power losses in the designated transformer. This will have an effect on the resulting power factor as long as the power factor’s measurement point is placed after the transformer. In other words, when selecting the power factor at the substation input, varying the power station transformer losses will have an effect on the resulting power factor at the inverter's output. Whereas, selecting it at the substation output will mean that any variation in the power station or the substation transformer losses will affect this resulting inverter power factor.
These two parameters (transformer losses and the resulting inverter power factor) are actually directly proportional, so increasing one will increase the other. This direct proportionality is due to the relation between transformer active and reactive power losses. The higher these active power losses are, the lower is the reactive power that needs to be compensated, and thus the resulting power factor at the inverter output will be higher.
What does placing a value of Zero in the Transformer Losses imply?
Just as mentioned above, modifying the transformer’s iron and copper losses will affect both the active and the reactive power. Placing a value of zero for these two losses in pvDesign will mean that the active power loss will be canceled out, but the reactive power loss will still be taken into account as it depends on various other factors. This will cause the reactive power loss to increase and thus the resulting inverter power factor to decrease.
Is there a way for me to Disable both the Transformer's Active and Reactive Power Losses?
In order to disable both the transformer active and reactive power losses at the same time, simply disable the respective option in pvDesign. This, obviously, will not reflect the actual functioning of a transformer, as now, the transformer will be an ideal one with no losses incurred. In reality, there are always going to be both active and reactive power losses in every transformer, and for this reason, we highly recommend that you keep this option enabled. Disabling these losses completely will result in a higher inverter output power factor.
It will also increase the PV plant’s PR and its specific production. This is due to some losses being lower when this option is disabled, mainly the inverter power factor loss, and on a smaller scale, different wiring losses.
Why does the Energy Report sometimes show a Different Power Factor from the one I selected?
An interesting aspect to highlight is that the final calculated power factor which appears in the Energy Report could be different from the one that you specify. In order to understand why this occurs, it is necessary to know how this whole calculation flow takes place.
While selecting the equipment and determining the different parameters of your project within pvDesign, the software won’t know how much total capacity your PV plant has until you reach the “Layout” tab. In order to calculate the inverter’s resulting power factor, however, pvDesign needs to know this total capacity. So in order to get this information, it estimates the total capacity of your PV plant based on its size and electrical configuration.
It then starts applying the different losses in the transformers (active and reactive power losses) and the wiring/cables (active power losses) until it reaches the inverter output. So it basically starts from the selected power factor measurement point and goes back towards the inverters. This result is now used to calculate the power factor at three different points: the substation’s input, its output, and the grid connection point. This calculation is done in the forward direction using the previous result and then applying it to the actual total capacity of your PV plant which at this point (simulation window) is accurately calculated. This could cause some discrepancies between the predetermined power factor value and the one that appears in the Energy Report.
What does Enabling the Power Factor exactly do?
As mentioned above, enabling the power factor in pvDesign will cause more inverters to be installed in order to compensate for the reactive power. This can be seen better through the example of Figure 3. Figure 3 mainly shows how in order to maintain the same total capacity in your PV plant at a lower power factor, more inverters need to be installed.
Figure 3 - A PV plant at two different power factors.
This can be understood better by observing Equation 1.
- PDC is the peak DC power output of the PV plant.
- PAC is the nominal AC power output of the PV plant. PAC = SAC * Power factor (where SAC is the total apparent AC power output of the plant).
Thus, when the power factor is less than 1, PAC becomes smaller thus increasing the DC/AC ratio. Our goal is to always maintain the peak power and the DC/AC ratio fixed. This is why the denominator of the previous equation should be increased. Since the power factor is also fixed, we are only left with the option of increasing the AC power which can be done by increasing the number of inverters.
This is how enabling a power factor works in pvDesign. We hope that you have enjoyed the ride and got a clear understanding of the different aspects to be considered regarding this topic. Take care!!!
If you have any questions, please feel free to contact us at email@example.com.